Outputs2 BO + 2 AO + 2 CO
Communications BusRS-485, field selectable between BACnet MS/TP and N2 communications: 3-wire FC Bus between the supervisory controller and field controllers; 4-wire SA Bus between field controller, network sensors, and other sensor/actuator devices, includes a lead to source 15 VDC supply power (from field controller) to bus devices.
Power Consumption14 maximum VA
Operating Ambient Conditions0 to 50°C (32 to 122°F); 10 to 90% RH noncondensing; Pollution Degree 2
ProcessorRX631 32-Bit Renesas microcontroller
Memory4 MB flash memory and 1 MB RAM
TerminationsInput/Output: Fixed Screw Terminal Blocks
FC Bus, SA Bus and Supply Power: 3-wire and 4-wire Pluggable Screw Terminal Blocks. SA Bus Port: RJ-12 6-pin Modular Jacks.
MountingHorizontal on single 35 mm DIN rail mount (preferred), or screw mount on flat surface with three integral mounting clips on controller
Housing MaterialABS and polycarbonate UL94 5VB; Self-extinguishing.
Housing Protection ClassIP20 (IEC529)